Search RV-Coach Online
|email Cliff reply to message post new message search forums|
ATTENTION: DO NOT POST ADS IN FORUMS!|
All Postings that advertise items for sale will be deleted from the Discussion Forum. You may post sale items for free in the Classifieds section. Sign up now.
|All Messages in Thread||Author||Date|
|Coleman 8534D Heat Pump-Gen Surges||Cliff||6-16-17|
|I have the Mach 8534D8796. With 5500 generator running, the front air conditioner causes the generator to surge about every 30-45 seconds and the amps increase to 48-58. It continuously goes through that cycle. The rear unit works just fine. Maybe one of the compactors? Thanks...|
|Re: Coleman 8534D Heat Pump-Gen Surges||Bubba The Bus Tech||6-16-17|
|I doubt the AC is cooling. |
I bet the Compressor is seized solid and the AC needs replacing.
The 48 amp draw is the compressor trying to start and the overload tripping out.
|Re: Coleman 8534D Heat Pump-Gen Surges||Cliff||6-25-17|
|Figured it out. Found the start hard start capacitor to be bad...actually burned the wire off. Replaced and working fine.|